We will attend 117th The Chiness Export Commodities Fair (Canton Fair) from April 15th~19th ,Welcome to visit us for further business . We will show our newest UPS (modular ups )and solar inverter there ,and will have some gifts for you Date: April 15 to 19 Booth No: Hall 10.3,K30 See you at Canton Fair 2015,Guangzhou, China
1.Use of AC voltage regulator After using UPS power supply, there is no need to add AC voltage regulator. If it must be added, it should be added to the front level of UPS, that is, the mains power first passes through the AC voltage regulator, then through the ups, and then to the load.
2.Battery balanced charging skills At present, valve regulated lead-acid battery (VRLA) used in many ups power supply is called maintenance free battery from the beginning, which gives users a misunderstanding that it seems that this battery is durable and does not need maintenance at all. Under this kind of misleading, many users have not carried out maintenance and management since they installed the battery. When the battery in UPS power supply meets the following conditions, the battery shall be charged evenly: when the terminal voltage is lower than the specified calibration voltage due to excessive discharge. For 12 V small sealed lead-acid batteries, the discharge calibration voltage is 10.5 V; for 24 V batteries, the final discharge voltage is 21 V; for 96 V batteries, the discharge calibration voltage is 85 v. The battery is not charged in time after discharge; the battery is idle for a long time. When the power supply is interrupted, the battery with continuous floating charge will release nearly half of its capacity.
3.Do not use diesel generators UPS should not be powered by diesel generator because its frequency is often unstable, which affects the normal operation of ups.
4.Pay attention to the safe operation of operators When connecting the output power supply to UPS, attention should also be paid to safety. Since the output voltage and current of ups are relatively large, it is necessary to pay attention to safety when connecting the output power supply to prevent the occurrence of electric shock accidents. When replacing the battery, turn off the UPS power supply and disconnect from the mains power supply. Use a screwdriver with insulated handle. Do not put tools or other metal objects on the battery. When connecting the battery cable, it is normal to have small sparks at the connector, which will not harm personal safety and UPS power supply. Do not short circuit or reverse connect the positive and negative electrodes of the battery. When replacing the battery, it is not suitable to replace it partly, but to replace it as a whole. In addition, it is forbidden to use batteries with different amperage and different brands.
5.Real time monitoring At present, all intelligent UPS have operability characteristics such as communication with microcomputer and program control. When the corresponding software is installed on the microcomputer and connected to UPS through serial / parallel port, the program can be used to communicate with ups. Generally, it has the functions of information inquiry, parameter setting, timing setting, automatic shutdown and alarm. Then, the UPS is connected to the computer through the special serial port control cable, and then through RS232 and RS485 protocol communication, the ups can automatically shut down when there is no mains power input and the power is low. It can monitor multiple UPS connected to multiple serial ports at the same time. Among them, through RS232 protocol, a serial port can only connect one UPS, through RS485 protocol, a serial port can connect 256 ups at most.
1.True double-conversion 2.DSP technology guarantees high performance 3.Output power factor 0.9 4.Wide input voltage range (110-300 VAC) 5.Active power factor correction in all phases 6.50Hz/60Hz frequency converter mode 7.ECO mode operation for energy saving 8.Accepts dual-mains inputs 9.Emergency power off function (EPO) 10.Generator compatible 11.SNMP+USB+RS-232 multiple communications 12.3-stage extendable charging design for optimized battery performance 13.Adjustable battery numbers 14.Maintenance bypass available 15.Optional N+X parallel redundancy 16.Optional isolation transformer offers full isolation and complete common mode noise rejection
On Oct 15th 2019, as one of the most important trade promotion platforms for Chinese enterprises to expand the global market, Canton Fair in Guangzhou focused on highlighting innovation driven, and “independent brand” became a high-frequency word of Canton Fair.
Xu Bing, a spokesman for the Canton Fair and deputy director of the China Foreign Trade Center, said that the domestic and foreign environment faced by China’s foreign trade development this year is more complex and uncertain. The majority of exhibitors accelerated quality improvement and innovation, and continued to make efforts in technology research and development, product innovation, brand cultivation, etc., with high technology, high quality, high added value and independent brand products emerging.
Many independent innovative R & D products are welcomed by the market. At the same time, purchasers are less sensitive to price and pay more attention to the technology, brand, quality and service of products.
In this exhibition, Sorotec‘s products have attracted many customers and been widely praised. Especially Revo II. Revo II is a hybrid pure sine wave solar inverter. Its particular touch screen makes it more convenient to operate. It can parallel up to 9 pcs. The maximum power is 49.5KW. It has four working modes. Especially in the “Solar+AC” working mode, the solar and AC mains can charge the battery and power the loads together. It is the maximum use of the solar energy. The solar energy utilization is over 15% than other solar inverter. Revo series can start and work without battery, and also can work with lithium battery. This product has a strong comprehensive competitiveness.
Sorotec not only has the most advanced scientific research technology in the field. The products are of high gold content. And Sorotec is willing to accept and create new things. This has been unanimously recognized by all customers.
Due to the high integration, compact overall structure and large heat dissipation, the hybrid inverter requires high temperature, humidity and dust content in the installation environment. When installing the solar inverter, it must provide a good operating environment for the inverter. The working ambient temperature of the inverter is rated at 40 ℃. If the ambient temperature is higher than 40 ℃ ~ 50 ℃, the rated current must be reduced. Otherwise, the temperature rise of the device will be too high, which will increase the possibility of device damage (especially IGBT power module), and have a great impact on normal and safe operation. If the working environment of the inverter fails to meet the requirements of the inverter on the working environment, it will cause high failure rate of the inverter, affect the long-term, reliable and safe operation, resulting in unnecessary economic losses. Therefore, the following matters should be paid attention to in the application of the inverter.
The inside of the inverter is a high-power electronic component, which is easily affected by the working temperature. The product is generally required to be 0-55 ℃, but in order to ensure the safety and reliability of the work, it should be considered to leave room for use, preferably controlled below 40 ℃. If the inverter is installed in the inverter cabinet, it shall be installed on the upper part of the cabinet and strictly comply with the installation requirements in the product manual. It is absolutely not allowed to install the heating element or the element easy to heat against the bottom of the inverter.
When the temperature is too high and the temperature changes greatly, condensation is easy to occur inside the inverter, and its insulation performance will be greatly reduced, or even lead to short circuit accidents. If necessary, desiccant and heater must be added to the inverter cabinet. The surrounding humidity of the inverter shall be below 90%. If the surrounding humidity is too high, the electrical insulation will be reduced and the metal part will be corroded. If restricted by the installation site, the inverter shall not be installed in a place with high humidity, and the cabinet of the inverter shall be sealed as far as possible. In order to prevent condensation when the inverter stops, a convection heater should be added.
If the concentration of corrosive gas is large, it will not only corrode the leads and printed circuit boards of components, but also accelerate the aging of plastic components and reduce the insulation performance. In this case, the inverter cabinet should be made into a closed structure and air exchange. There shall be no corrosive, explosive or combustible gas, dust and oil mist around the inverter. If there are explosive and combustible gases in the surrounding environment where the inverter is installed, there are relays and contactors that are easy to generate sparks in the inverter, so fire or explosion accidents may be caused sometimes. If there is dust and oil mist around the inverter, its adhesion and accumulation in the inverter will lead to the decrease of insulation; for the inverter with forced air cooling, the temperature in the inverter will rise abnormally due to the filter blockage, so that the inverter cannot operate stably.
4.Vibration and shock.
When the inverter cabinet is subject to mechanical vibration and impact, it will cause poor electrical contact. At this time, in addition to improving the mechanical strength of the inverter cabinet, away from the vibration source and impact source, the anti-seismic rubber pad shall be used to fix the inverter cabinet and electromagnetic switch and other components that generate vibration. The vibration resistance of the inverter should be different in different types. When the vibration exceeds the allowable value of the inverter, the fastening part of the components will be loose and the relay and contactor will act wrongly, which often leads to the unstable operation of the inverter. For the vibration situation that can be foreseen in advance, the vibration of inverter should be fully considered.
5.The altitude of inverter application is usually below 1000m.
If the altitude is high, the air pressure will be high, which is easy to cause insulation damage. In addition, the cooling effect of high elevation also decreases, so it is necessary to pay attention to the temperature rise of inverter.
1.Touch screen display 2.PV and utility power take the load at same time(can setting) 3.Output power factor PF=1.0 4.On&Off Grid with energy storage 5.Energy generated record,load record,history information and fault record 6.Language and time setting 7.Structure with dust filter 8.AC charging and AC output time setting 9.Charging voltage and charging current timing 10.External Wi-Fi device optional 11.Parallel operation with up to 6 units only available for 3kW/4kW/5kW 12.Connected with battery optional 13.Wide PV input range 120-450VDC 14.Independent CPU 15.MAX PV Array power 4500W 16.Solar and Utility supply power to the load when solar power is not sufficient to load
The 7th Military World Games opened in Wuhan, Hubei Province on the evening of October 18, 2019. The Games will last 10 days from October 18 to 27, 2019.
The 7th Military World Games is the first comprehensive international military sports event hosted by China, with the largest scale in the past and the largest international sports event held by China after the Beijing Olympic Games. 9308 military athletes from 109 countries will compete and enhance friendship in Wuhan. As the host country, China has set up a sports delegation of 553 athletes, the largest in the history of our country.
It’s a great honor for soled to participate in the power security system of the games. SOROTEC GP9335C series online UPS provides power support for Wuhuan sports center.
During the military games, SOROTEC sent many engineers to the venue all day, recording the ups operation status in detail, ensuring that the power supply system is uninterrupted for 24 hours, providing stable, safe and reliable power support for the venue.
SOROTEC GP9335C series online UPS adopt advanced intelligent design concept, and are successfully applied in military system, electric power industry, PetroChina system, medical field, banking system, chemical industry, rail transit, political and mining fields, large-scale events, etc., all of which are well received by users.
■Use advanced 6th generation DSP and full digital control technologies to realize higher system stability. ■Output power factor is 0.9, carrying capacity than conventional UPS with 10% above, as users reduce investment cost. ■Advanced distributed active parallel technology can realize parallel operation of 6PCS UPS units without the need of centralized bypass cabinet. ■6-inch extra large LCD that can display 12 language ( Chinese ,English,Russian,Spanish,French and so on). ■Extra wide input voltage and frequency range make it adapt to severe power grid environment. ■Intelligent battery management maintains battery automatically to prolong the battery life. ■Standard input/output filter improves the system EMC performance. ■Extra strong capability to withstand output overload and short circuit, ensuring the system stability and system safety under extreme conditions. ■Layered independently-sealed ventilation channel and re-dundant fan, circuit boards with protective paints and a dust filter embedded make it highly efficient to dissipate heat and protect the product effectively under severeenvironment.
Manufacturers and users of UPS power supply system have long noticed the matching problem between generators and UPS, especially the harmful effects of current harmonics generated by rectifiers on power supply systems such as voltage regulators of generators and synchronous circuits of UPS. Therefore, the technicians designed the input filter and applied it to UPS, and successfully controlled the current harmonics in UPS application. These filters play a key role in UPS compatibility with generators.
In fact, all input filters use capacitors and inductors to absorb the destructive current harmonics at the UPS input. The design of the input filter takes into account the percentage of all possible harmonic distortion inherent in the UPS circuit and at full load. Another benefit of most filters is to increase the input power factor of UPS with load. However, another consequence of the application of input filters is to reduce the overall efficiency of UPS. Most filters consume about 1% UPS power. The design of input filters has been seeking a balance between advantages and disadvantages.
In order to improve the efficiency of UPS system as much as possible, UPS engineers have recently improved the power consumption of input filters. The improvement of filter efficiency depends largely on the application of IGBT (Insulated Gate Transistor) technology to UPS design. The high efficiency of IGBT inverters leads to the redesign of UPS. The input filter can absorb some current harmonics and a small part of active power. In short, the ratio of inductance factor to capacitance factor in the filter is reduced, and the volume of UPS is reduced and the efficiency is improved. The compatibility between UPS and generators is another problem.
1.Superior energy saving and environment-friendly: Efficiency > 96% at 50%-75% rated load, and > 95% at 25% rated load; Input PF > 0.99,input THDi<3%. 2. Superior capability of powering load: Output PF is 0.9 or 1, no need of power deration with load of leading or lagging PF. 3. Easy-to-install: Top or bottom cabling, no need of input cabling cabinet. 4. Easy-to-maintain: Full front access, UPS, failed part can be replaced shortly. 5. Easy-to-modify: The number of battery cells can be configured flexibly, so the original batteries can be used when modifying the legacy system; moreover, the battery cell can be replaced in time when it fails without interrupting the normal operation of UPS. 6.6-inch extra large LCD that can display 12 language (Chinese ,English ,Russian, French ,Spanlish and so on). 7.Provide large LCD touch screen (optional). 8.Each UPS modules provide 4.5KW charge capacity. equivalent to 10 to 12A. 9.On-Line Double Conversion, fully isolating the influences of power grid pollution and power failure from utility power supply and diesel generator to load. 10. Advanced DSP full digital control technologies realize higher system stability, online capacity expansion and maintenance. 11.Advanced distributed active parallel technology realizes parallel operation of 4 UPS units and online capacity expansion without centralized bypass cabinet. 12.Digital load sharing technology features extra low cross current and extreme high system reliability in parallel operation. 13.Adaptive to severe power grid environment due to extra wide input voltage and frequency ranges. 14.Extra strong capability to withstand output overload and short circuit, ensuring the system stability and system safety at limit conditions. 15 Intelligent battery management maintains battery automatically to prolong the battery life. 16. Efficient heat dissipation and effective protection under severe environment due to its independent layer-sealed ventilation channel and redundant fan design, as well as the paint-protected circuit boards and built-in dust filter. 17.Applicable voltage south America.