Due to the high integration, compact overall structure and large heat dissipation, the hybrid inverter requires high temperature, humidity and dust content in the installation environment. When installing the solar inverter, it must provide a good operating environment for the inverter. The working ambient temperature of the inverter is rated at 40 ℃. If the ambient temperature is higher than 40 ℃ ~ 50 ℃, the rated current must be reduced. Otherwise, the temperature rise of the device will be too high, which will increase the possibility of device damage (especially IGBT power module), and have a great impact on normal and safe operation. If the working environment of the inverter fails to meet the requirements of the inverter on the working environment, it will cause high failure rate of the inverter, affect the long-term, reliable and safe operation, resulting in unnecessary economic losses. Therefore, the following matters should be paid attention to in the application of the inverter.
The inside of the inverter is a high-power electronic component, which is easily affected by the working temperature. The product is generally required to be 0-55 ℃, but in order to ensure the safety and reliability of the work, it should be considered to leave room for use, preferably controlled below 40 ℃. If the inverter is installed in the inverter cabinet, it shall be installed on the upper part of the cabinet and strictly comply with the installation requirements in the product manual. It is absolutely not allowed to install the heating element or the element easy to heat against the bottom of the inverter.
When the temperature is too high and the temperature changes greatly, condensation is easy to occur inside the inverter, and its insulation performance will be greatly reduced, or even lead to short circuit accidents. If necessary, desiccant and heater must be added to the inverter cabinet. The surrounding humidity of the inverter shall be below 90%. If the surrounding humidity is too high, the electrical insulation will be reduced and the metal part will be corroded. If restricted by the installation site, the inverter shall not be installed in a place with high humidity, and the cabinet of the inverter shall be sealed as far as possible. In order to prevent condensation when the inverter stops, a convection heater should be added.
If the concentration of corrosive gas is large, it will not only corrode the leads and printed circuit boards of components, but also accelerate the aging of plastic components and reduce the insulation performance. In this case, the inverter cabinet should be made into a closed structure and air exchange. There shall be no corrosive, explosive or combustible gas, dust and oil mist around the inverter. If there are explosive and combustible gases in the surrounding environment where the inverter is installed, there are relays and contactors that are easy to generate sparks in the inverter, so fire or explosion accidents may be caused sometimes. If there is dust and oil mist around the inverter, its adhesion and accumulation in the inverter will lead to the decrease of insulation; for the inverter with forced air cooling, the temperature in the inverter will rise abnormally due to the filter blockage, so that the inverter cannot operate stably.
4.Vibration and shock.
When the inverter cabinet is subject to mechanical vibration and impact, it will cause poor electrical contact. At this time, in addition to improving the mechanical strength of the inverter cabinet, away from the vibration source and impact source, the anti-seismic rubber pad shall be used to fix the inverter cabinet and electromagnetic switch and other components that generate vibration. The vibration resistance of the inverter should be different in different types. When the vibration exceeds the allowable value of the inverter, the fastening part of the components will be loose and the relay and contactor will act wrongly, which often leads to the unstable operation of the inverter. For the vibration situation that can be foreseen in advance, the vibration of inverter should be fully considered.
5.The altitude of inverter application is usually below 1000m.
If the altitude is high, the air pressure will be high, which is easy to cause insulation damage. In addition, the cooling effect of high elevation also decreases, so it is necessary to pay attention to the temperature rise of inverter.
1.Touch screen display
2.PV and utility power take the load at same time(can setting)
3.Output power factor PF=1.0
4.On&Off Grid with energy storage
5.Energy generated record,load record,history information and fault record
6.Language and time setting
7.Structure with dust filter
8.AC charging and AC output time setting
9.Charging voltage and charging current timing
10.External Wi-Fi device optional
11.Parallel operation with up to 6 units only available for 3kW/4kW/5kW
12.Connected with battery optional
13.Wide PV input range 120-450VDC
15.MAX PV Array power 4500W
16.Solar and Utility supply power to the load when solar power is not sufficient to load