1.The power of UPS generally refers to the output power. The input power is bigger than the rated power, especially when the battery has discharged after a period of power stopping. The input rectifier not only supplies power to the load, but also charges the battery. The maximum current can reach 1.3 times of the rated current. If the battery pack capacity is particularly large, and the host is equipped with a charging module, the current will be greater.
2.UPS itself is a kind of non-linear load, which will produce some harmonic current feedback to the input grid, and will increase the temperature of the generator ball. If the generator load ratio is too high, it may burn the ball.
3.The load behind UPS to the generator is all selected by the internal circuit of on grid UPS to be battery or city power/power generation. It is one-time loading. There is no soft start or other way. If UPS is loaded at 80% load and the impulse current is calculated at three times, all of them exceed the rated output of the generator configured at two times. The frequency and voltage of the generator will decrease at this time. UPS detects this change and will immediately switch to the battery for power supply.
Therefore, the capacity of the generator with UPS should be large enough, not as simple as 2 times the capacity. It should be configured according to the specific situation.
■Use advanced 6th generation DSP and full digital control technologies to realize higher system stability.
■Output power factor is 0.9, carrying capacity than conventional UPS with 10% above, as users reduce investment cost.
■Advanced distributed active parallel technology can realize parallel operation of 6PCS UPS units without the need of centralized bypass cabinet.
■6-inch extra large LCD that can display 12 language ( Chinese ,English,Russian,Spanish,French and so on).
■Extra wide input voltage and frequency range make it adapt to severe power grid environment.
■Intelligent battery management maintains battery automatically to prolong the battery life.
■Standard input/output filter improves the system EMC performance.
■Extra strong capability to withstand output overload and short circuit, ensuring the system stability and system safety under extreme conditions.
■Layered independently-sealed ventilation channel and re-dundant fan, circuit boards with protective paints and a dust filter embedded make it highly efficient to dissipate heat and protect the product effectively under severeenvironment.