1.Superior energy saving and environment-friendly:
Efficiency > 96% at 50%-75% rated load, and > 95% at 25% rated load; Input PF > 0.99,input THDi<3%.
2. Superior capability of powering load:
Output PF is 0.9 or 1, no need of power deration with load of leading or lagging PF.
Top or bottom cabling, no need of input cabling cabinet.
Full front access, UPS, failed part can be replaced shortly.
The number of battery cells can be configured flexibly, so the original batteries can be used when modifying the legacy system; moreover, the battery cell can be replaced in time when it fails
without interrupting the normal operation of UPS.
6.6-inch extra large LCD that can display 12 language (Chinese ,English ,Russian, French ,Spanlish and so on).
7.Provide large LCD touch screen (optional).
8.Each UPS modules provide 4.5KW charge capacity. equivalent to 10 to 12A.
9.On-Line Double Conversion, fully isolating the influences of power grid pollution and power failure from utility power supply and diesel generator to load.
10. Advanced DSP full digital control technologies realize higher system stability, online capacity expansion and maintenance.
11.Advanced distributed active parallel technology realizes parallel operation of 4 UPS units and online capacity expansion without centralized bypass cabinet.
12.Digital load sharing technology features extra low cross current and extreme high system reliability in parallel operation.
13.Adaptive to severe power grid environment due to extra wide input voltage and frequency ranges.
14.Extra strong capability to withstand output overload and short circuit, ensuring the system stability and system safety at limit conditions.
15 Intelligent battery management maintains battery automatically to prolong the battery life.
16. Efficient heat dissipation and effective protection under severe environment due to its independent layer-sealed ventilation channel and redundant fan design, as well as the paint-protected
circuit boards and built-in dust filter.
17.Applicable voltage south America.
IDC (Internet Data Center) , computing center, ISP (Internet Service Provider ),Telecom,Finance bank and securities,Tax, hospital system, industrial automation, precision equipment, etc.
|Input voltage||380V/400V/415AC(Optional South America 208v)|
|Input Frequency Range||50/60Hz|
|Power Factor||Full load>0.99 ,Half load >0. 98|
|Input power soft-start fantion||5-30s settable|
|Input Voltage Ranges||228V-476V-20%- +25% Full load linear derating at -25% - -40%; can take 70% load at -40%|
|Battery Voltage||±240VDC(Default),12V Battery30-40pcs can be choose|
|Charge Voltage accuracy||± 1%|
|Bypass Input voltage||380/400/415VAC 3-phase 4-wire|
|Voltage Ranges||Default value is -20%-+15%, -40%, -30%, -10% - +10%, other ranges can be set viasoftware|
|Overload Capacity||150%,long term operation,150%
|Inverter Output Voltage||380/400/415VAC 3-phase 4-wire|
|Voltage Accuracy||± 0.5%(balanced load), ± 1% (unbalanced load)|
|THDV||THDV<1%(linear load), THDV<3%(nonlinear load)|
|Three Phase Angle accuracy||120°c ± 0.5°c|
|Current Crest Ratio||0.12569444444444|
|Transfer Time||0ms,15ms(ECO Mode)|
|Mains synchronization range||±2Hz(Default value) adjustable with step of 0.5Hz within range of +/- 0.5Hz - 3Hz|
|Communication Ports||RS232,RS485,dry contact,SNMP card,EPO,generator port|
|System efficiency||> 96% at load above 50%, >95% at load above 25%|
|Operation Temperature||0-40 °c|
|Storage Temperature||-25 °c -70 °c (without battery)|
|Noise(dB)||55-62dB,Adjusted with load|
|Weight||module :PM10||10KVA power module :20KG|
|module :PM20||20KVA power module :35KG|
|module :PM30||30KVA power module :35KG|
|Dimendion(W XD XH)mm||3module cabinet||600*900*1135|
MPS9335C series power system structure is extremely flexible, the concept of power modular designing can be easily removed at runtime and installed without affecting system operation and output, implement investment planning with the need to expand, allowing users to achieve dynamic growth with business development, it saves customer’s costs for initial equipment purchasing and future expansion. When user estimated UPS capacity, often underestimated or high expected, MPS9335C 10-300KVA High Frequency Online Modular Type UPS can solve the above problems effectively, help user to carry out construction and investment in phase under the condition that future development direction is not clear. When users want to add load to the UPS, only adding the required number of modules for expansion.
The power module of Modular type UPS uses double conversion on-line structure, including the rectifier, inverter, charger, control circuit, and the input output battery bus of the circuit breaker. With input power factor compensation. All modules can be replaced online hot swap, to provide the highest level of availability, maintainability.
The modular type UPS host control module adopts industrial BUS CAN bus control structure, which is controlled by two redundant modules to complete the control and management of the system. A control module failure will not affect the normal operation of the system. Control module can be online hot swap replacement. Power modules are connected in parallel by the control module centralized management, in accordance with the unified and machine parameters to run, a power module fault can automatically exit the parallel system, not on the entire parallel system.
The modular type UPS system adopts an independent static bypass module, which does not use a number of static bypass structures, so as to avoid the overload damage caused by multiple bypass of bypass. The accuracy of the output voltage of the module is + 1%, and the circulating current is <1%.
Standard SNMP card, using HTTP protocol, SNMP protocol, TELNET protocol, etc.. The modular type UPS in the city state of electricity, battery state, the state of the bypass, inverter, the self state, boot state and input voltage, output voltage, percentage of load, the input frequency, the voltage of the battery, battery capacity, battery discharge time, UPS machine temperature, surrounding temperature and so on UPS run at a glance, to improve the efficiency and quality of the modular type UPS power supply security system management. Selection of open windows2000/windowsXP/windows2003 windowsNT/ operating system platform.
The temperature and humidity sensor can be selected, and the multifunctional network card is inserted, and the temperature and humidity monitoring and alarming of the computer room environment can be realized through the network.