Data center, bank station, network , telecom station, office, automatic equipment,monitor equipment, control system
1.Battery voltage can be choice depend on capacity , can satisfy different requirement.
2.Convenience to get more back up time and lower system invests
3.Convenience to save cost of battery
4.Intelligent battery monitors
Charge current can be adjust
5.Standant charge current 4A
6.Support more discharge time and more capacity battery for 8A charger
Input topology design
7.Support three phase input or single phase input for three phase online high frequency UPS
8.Super wide input voltage and frequency range suitable for bad power electirc environment
9.Digital control DSP technology and best power component make the system safe and reliable
1.Stable parallel control technology make sure current sharing to 1%
2.Select trip technology can avoid and isolation system fault then improved system availability
3.Flexible extension capacity and redundance management that can satisfy all kinds of requirements
4.Support maximum 3 units for parallel working
5.On line mode provides higher system availability
6.High efficiency mode provides more economic operation
7.Frequency conversion provides more stable output
1.Output power factor is 0.9 that mean can take more load, if you take same load that can get higher reliability.
Input power factors up to 0.99
2.Three phase input model support three phase PFC , input THDI<5%
3.Output voltage regulation 1%, frequency regulation 0.1%, parallel current sharing 1%.
The efficiency up to 94%
4.Efficiency up to 93.5%when take the 30%load
5.ECO mode efficiency up to 98%
|HP9116C Plus 1-3KVA
|50HZ: (46~54HZ); 60HZ:(56HZ~64HZ)
|Linear load＜4％ Non-linear load＜7％
|110%~150% for 47-25 sec；150%~200% for 25 -300ms; >200% for 200m
|Current Crest Ratio
|0ms (AC mode→Battery mode)
|Efficiency(on line mode)
|7hrs to 90% of capacity
|Display input/output Voltage, Frequency, Battery voltag, Battery capacity, Loading rate.
|Smart RS232, SNMP(Optional),USB (Optional)
|Sea Level Elevation
|Noise Level (1m)
|Dimensions: Wx D x H )mm
The module online high frequency UPS integrates the advantages of centralized and decentralized power supply topology, introduced the concept of the regional power supply from the design. If separated in several areas of a large data center, in each region configure a set or two sets (redundant) 3A3 UPS power supply system, directly placed in the area near the load, power supply through the switchboard on the cabinet. In this way, each region is centralized power supply, centralized management, and among different region is the decentralized power supply independently, so is wiring. 3A3 online high frequency UPS power supply has the advantages of decentralized which is flexible configuration, allowing gradual investment, not easy to produce a large area of paralysis, but also has the advantages of centralized which is easy to manage.
Humanized operation interface and perfect power management software. Parallel operation system uses the big screen LCD as the operating interface, shows operation and information read. With the latest version of the monitoring software, power management becomes easier. If use the optional SNMP card, can be more remote monitoring.