■.Highly integrated outdoor electrical enclosure with strong housing ability, can be used as equipment cabinet, battery cabinet or integrated cabinet
■.Well environmental adaptability with IP55 class protection and full ranges of temperature control system
■.Precise and separate temperature control reduces energy cost
■.Multi-layer panel structure makes less heat absorbance and saves energy
■.Anti-theft design and earthquake protection tests ensure outdoor electrical enclosure and equipments safety
■. Well environmental adaptability with IP55 class protection
■.Support delivery in whole or in parts with no limits to installation scenario
■Mini-shelter includes power system cabinet, power system, AC/DC distribution unit, monitor unit, and heater, distribution cables, battery and sensors are optional.
■Cabinet: one unit one cabinet, one unit two cabinet, two units three cabinets, three units three cabinets.
■Power system: ETP48200A , rectifiers
■AC/DC distribution unit: AC distribution and DC distribution unit are optional
■Heater: it is optional, and it is used in cold areas.
■Distribution cables: ODF and DDF are optional.
■Monitor unit: ETP48200A with SMU02B monitor module, battery temperature sensor, environment temperature and humidity sensor, smoke sensor and water sensor, and so on.
■Battery: the type of battery is determined by load and the backup time.
Used in the manufacture of outdoor electrical enclosure outside the plate, the thickness is greater than or equal to 1.5 mm galvanized plate, hot galvanizing plate after welding shall be outdoor powder coating. Temperature control device for outdoor electronic enclosure type heat radiation with hot galvanizing plate for plate, temperature control device for refrigeration cabinet use is greater than or equal to 1.5 mm galvanized plate with 10mm insulation cotton structure into a sheet. The base outdoor electrical cabinets are made of cold rolled steel plate thickness not less than 2mm, after welding galvanizing surface treatment. For the metal outdoor electrical cabinets, after or after surface treatment, should have the ability to resist corrosion and electrochemical reaction. Non metal parts (including insulated wire, cable and foam material) should be flame retardant materials, the combustion of flame retardant should be able to pass the test requirements.