The economic mode of UPS has great advantages, but the latest development of silicon carbide technology could offset the economic advantages of the mode, the transistor is the traditional silicon controlled device for UPS, insulated gate bipolar transistor (IGBT) function more and more powerful and reliable.
The UPS with IGBT device has an obvious disadvantage, the faster the switching speed is (to obtain higher accuracy), the higher the power loss. This is mainly because the upper limit of the module efficiency is 96.8%, and the efficiency of the dual conversion UPS can be increased to 98%~99% theoretically by using SiC devices.
The synthesis of silicon carbide powder has been mass production since 1893, the initial cost of manufacturing IGBT by using silicon carbide is very high, but the energy-saving effect is very significant, and all these are not the key to the power grid load transfer, will not increase the risk of power conversion.
At the module level, silicon carbide has two advantages: Smaller chip size and lower dynamic loss. At the system level, these advantages can be exploited in many ways. Low dynamic losses lead to a significant increase in output power, providing an opportunity to reduce weight and volume. It is worth mentioning that power increase can be achieved without additional cooling capacity, because compared with SCR, reduce the loss brought silicon carbide practical, can get higher output power under the same cooling condition. Low power loss can improve energy efficiency, allowing the design of more efficient inverters, so the UPS will be more efficient energy saving.
Therefore, if silicon carbide is used, UPS can no longer be operated in an economy mode, you can even eliminate online interactive UPS, as the user is able to less than 1% of the energy loss, it can get the comprehensive protection of voltage and frequency protection, who will need UPS to run in the economic model?
SOROTEC MPS9335C 10-1200KVA With Switch Cabinet Modular UPS Systems
1.Superior energy saving and environment-friendly: Efficiency > 96% at 50%-75% rated load, and > 95% at 25% rated load; Input PF > 0.99,input THDi<3%.
2.Superior capability of powering load: Output PF is 0.9 or 1, no need of power deration with load of leading or lagging PF.
3.Easy-to-install: Top or bottom cabling, no need of input cabling cabinet.
4.Easy-to-maintain: Full front access, UPS, failed part can be replaced shortly.
5.Easy-to-modify: The number of battery cells can be configured flexibly, so the original batteries can be used when modifying the legacy system; moreover, the battery cell can be replaced in time when it fails without interrupting the normal operation of modular UPS.
6.6-inch extra large LCD that can display 13 language (Chinese ,English ,Russian, French ,Spanlish and so on).
7.Provide large LCD touch screen (optional).
8.Each UPS modules provide 4.5KW charge capacity. equivalent to 10 to 12A.
9.On-Line Double Conversion, fully isolating the influences of power grid pollution and power failure from utility power supply and diesel generator to load.
10.Advanced DSP full digital control technologies realize higher system stability, online capacity expansion and maintenance.
11.Advanced distributed active parallel technology realizes parallel operation of 4 UPS units and online capacity expansion without centralized bypass cabinet.
12.Digital load sharing technology features extra low cross current and extreme high system reliability in parallel operation.
13.Adaptive to severe power grid environment due to extra wide input voltage and frequency ranges.
14.Extra strong capability to withstand output overload and short circuit, ensuring the system stability and system safety at limit conditions.
15.Intelligent battery management maintains battery automatically to prolong the battery life.
16.Efficient heat dissipation and effective protection under severe environment due to its independent layer-sealed ventilation channel and redundant fan design, as well as the paint-protected circuit boards and built-in dust filter.
17.Applicable voltage south America.